The Raw Wastewater Pump Station provides preliminary treatment, raw wastewater pumping and flow metering. Preliminary treatment includes a channel monster for reducing of large debris size, screening for removal of smaller solids and grit removal of abrasive materials such as sand, silt and gravel.
Preliminary treatment protects downstream process equipment from excessive wear. The raw wastewater pumps lift the wastewater to an elevation which permits gravity flow through the remainder of the treatment plant. Flow metering is provided for routine plant operation and control purposes.
[Back to Top]
The selector basin provides the right enviornment for Biological Nutrient Removal to occur. The raw wastewater and activated sludge bacteria are moved through an anaerobic zone to force the PAOs (Phosphate Accumilating Organisms) to release phosphorus from their cells. When these bacteria are moved into an aerobic environment, they take in more phosphorus than they released, removing the phosphorus from the wastewater stream.
The rest of the selector basin is in an anoxic condition. Facultative bacteria (can breath both dissolved and combined oxygen) are forced to breath only combined oxygen. They strip off the oxygen molecules from nitrite (NO2) and nitrate (NO3) releasing nitrogen gas into the atmoshere, thus removing nitrogen from the wastewater stream (denitrification).
BlowersThe activated sludge process requires a dissolved oxygen level adequate to maintain the biological treatment process. Compressed air from the blower building is piped to the following areas:
- Aeration Basin
- Post Air Basin
- Selector Basin
Four 300 HP centrifugal blowers are available for providing the plant air.[Back to Top]
- In the 1st stage, a natural biological treatment process is used to remove the largest portion of the carbonaceous, organic material and for phosphorus uptake to occur.
- The next 2 stages also use the activated sludge biological treatment process to remove the remainder of the Biochemical Oxygen Demand (BOD) and Suspended Solids (SS) from the wastewater.
The clarifiers receive wastewater along with suspended activated sludge solids from the Aeration Basin. The clarifiers provide a quiescent area which permits the solids to settle to the bottom. Clarified water drains over the weir to the next treatment process.
Floating materials in the wastewater entering the clarifiers, such as grease or scum, will float to the surface. This material is skimmed from the surface and collected in the clarifier scum box. Good clarifier performance is essential to the proper operation of the treatment plant.
[Back to Top]
The Disinfection Building houses the controls for the UV system, required to disinfect the clarified wastewater following activated sludge treatment process. Disinfection is accomplished by treating the wastewater with sufficient UV to kill most of the bacteria remaining after biological treatment. The UV leaves no residual to be harmful to aquatic life in the receiving stream. The Disinfection Building includes the controls for the UV system and the effluent sampler.
The UV basin consists of 4 channels with 40 bulbs per channel. Each channel is rated for 4.25 MGD of wastewater from the clarifiers. The clarifier effluent flow is measured by an ultrasonic flow meter. Flow enters an influent box and splits between the 4 channels as needed to meet the 4.25 MGD per channel. The UV effect is nearly instantaneous, requiring little contact time.
UV SystemHigh-output, Low-pressure Ultra-Violet Light Disinfection System:
- Destroys bacteria (E. coli) viruses (hepatitis and polio), and other water-borne pathogens
- Destroys Giardia and Cryptosporidium which are resistant to chlorine
- Is environmentally friendly, reduced liability - is safe to handle, no toxic chemicals, no chlorine leaks
- Is more cost-effective than chlorine systems
- Produces no known disinfection by-products, unlike chlorine
- Reduces harmful micropollutants (such as herbicides and pesticides)
- Works at least 20 times faster than chlorine
Post Aeration BasinThe Post Aeration Basin is the final liquid treatment process. The purpose of the basin is to provide aeration of treated wastewater to raise the dissolved oxygen to a level meeting the discharge standard. Dissolved oxygen is necessary to sustain desirable forms of aquatic life in the receiving stream. Low dissolved oxygen levels in the plant effluent could degrade stream water quality.
[Back to Top]
Effluent Pump StationNormally, wastewater from the Post Aeration Basin flows over the basin effluent weirs and flows by gravity to the Little Sac River. When the river is at flood stage, however, water will back up into the plant to a level which will prevent gravity flow. Under these circumstances, the Effluent Pump Station must be put into operation to pump the flow into a high-water outlet chamber.
[Back to Top]
Effluent StructurePlant effluent is discharged into the Little Sac River from the Effluent Structure.
[Back to Top]
Return Sludge Pump Station
The Return Sludge Pump Station includes pumping systems for recirculating settled activated sludge from the clarifiers to the Aeration Basin, wasting activated sludge to the rotating drum thickeners and removing scum collected in the clarifiers. The pump station also includes equipment for non-potable water and compressed air. Finally, the pump station control room includes motor control centers for equipment in the pump station and the clarifiers.
Rotating Drum Thickeners
To control the treatment process, a portion of the activated sludge has to be removed daily. Waste activated sludge is pumped to two rotating drum thickeners were the sludge is concentrated to 5-7% total solids and pumped to the sludge storage basin.
Sludge Storage Basins
Sludge Storage Basins store sludge prior to being hauled to the south plant for digestion. They provide a means to store sludge during weekends and holidays when crews are not available to haul the sludge. Sludge Storage Basin No. 2 is covered with a clear span, self-supporting geodesic aluminum dome to contain odorous air. A 32-inch diameter odor control air collection pipe conveys the air from the sludge storage basin to the Bio-filter and carbon filter, to remove odors. Since Sludge Storage Basin No. 1 is not covered, it is held in reserve for emergency or testing situations only.